A NEW APPROACH TO FIGHTING FIRES MULTIFUNCTIONAL HIGH RISE BUILDINGS.
Intensive construction of multi-functional high-rise buildings, in the absence or inadequacy of providing a regulatory framework often results in higher costs for design and construction protivopazharnoy protect these structures. In this case, in order to ensure better protection of high rise involuntarily laid multiple overlapping systems protivopazharnoy protection.
Standalone Fire module container type. (APMKT)
General Director of NGO "Sopot".
Director General of TD "Ivhimprom"
The basis of the high-rise buildings fire suppression systems traditionally, like many years ago, laid the water systems, despite the fact that most designers know that the fire water inefficiently and that it is in the process of localization and suppression often causes much more damage to buildings, structures and property, rather than the fire itself.
APMKT entrance vestibule.
Internal layout APMKT.
"01 UNIFORM SERVICE RECOVERY "August 2006.
In our view, high-rise firefighting zdaniydolzhno and can be solved with the use of water and foam fire fighting, as it is high-rise buildings can be equipped with the necessary supply of water and foam, as well as the transportation system and supply foam to a potential fire hazard.
JSC NPO "Sopot", together with "Rybstroyinvest" and TD "Ivhimprom" conducted field tests APMKT goes directly to the construction site of a multifunctional skyscraper "Krylatskie Hills" in Moscow. The results exceeded all expectations. From APMKT connected to the power supply of the site, with UKTP "snowstorm" obtained the jet mechanical foam range of up to 50 m, the multiplicity of foam was 50. Based foam blowing agent P06TST of JSC "Ivhimprom" for a few seconds was covered an area of about 1000 square meters, with a layer of 0.3-0.5 m, which was held at the scaffolding, concrete area for 2-3 hours .
Such tests proved the feasibility of a rapid response to emerging high-rise buildings by the fire as the builders and the staff of the organizations maintaining the building.
The availability and effectiveness firefighting in buildings with mechanical foam was also confirmed during field tests in May 2006 in Volgograd, with foam fed into a burning building outside the building using UKTP "snowstorm", mounted on Automotive staircase AL-50. With the application was eliminated a simulated fire on the building area of over 100 square meters for 1-1.5 min..
Thus it is proved that the use of air-mechanical foam for fire fighting buildings can provide effective fire suppression and significantly reduce the amount of damages.
196070, RUSSIA, Saint-Petersburg, a/b 87
Phone/Fax : (812)464-61-41 e-mail:firstname.lastname@example.org
|News About Chronics Products Application Certificates Distibutors Clients Articles Contacts|